NOTE: When specifying the flow rate please take the clarifiers underflow rate into consideration. If, for example, you generate 250 GPM and expect a clarifier underflow rate of 10% you will have to have to specify a minimum flow rate of 275 GPM.
NOTE: Performance enhancement is to be achieved by the use of both co-current and counter current inclined plate packs as detailed in Metcalf & Eddy's "Wastewater Engineering - treatment and reuse" (chapter 5-33 through 5-38).
NOTE: Nothing is 100% efficient. Effective projected surface area will be established at 80% of total plate area unless manufacturer can provide verified "3rd party" fluid dynamic modeling studies and supporting multi-physics calculations to justify greater plate distribution efficiencies.
Follow this link to the "Common Engineering Specifications" document that covers all of the common specifications that relate to all HydroFlo Tech manufactured equipment.